|TIA-485-A (Revision of EIA-485)|
Approved: March 3, 1998
Reaffirmed: March 28, 2003
|Physical media||Balanced interconnecting cable|
|Network topology||Point-to-point, multi-dropped, multi-point|
|Maximum devices||At least 32 unit loads|
|Maximum distance||Not specified|
|Mode of operation||Different receiver levels:|
binary 1 (OFF)
(Voa–Vob < −200 mV)
binary 0 (ON)
(Voa–Vob > +200 mV)
|Available signals||A, B, C|
|Connector types||Not specified|
RS-485, also known as TIA-485(-A), EIA-485, is a standard defining the electrical characteristics of drivers and receivers for use in serial communications systems. Electrical signaling is balanced, and multipoint systems are supported. The standard is jointly published by the Telecommunications Industry Association and Electronic Industries Alliance (TIA/EIA). Digital communications networks implementing the standard can be used effectively over long distances and in electrically noisy environments. Multiple receivers may be connected to such a network in a linear, multidrop bus. These characteristics make RS-485 useful in industrial control systems and similar applications.
RS-485 supports inexpensive local networks and multidrop communications links, using the same differentialbalanced line over twisted pair as RS-422. It is generally accepted that RS-485 can be used with data rates up to 10 Mbit/s and distances up to 1,200 m (4,000 ft), but not at the same time. A rule of thumb is that the speed in bit/s multiplied by the length in metres should not exceed 108. Thus a 50 meter cable should not signal faster than 2 Mbit/s. Under some conditions it can be used up to data transmission speeds of 64 Mbit/s.
In contrast to RS-422, which has a single driver circuit which cannot be switched off, RS-485 drivers use three-state logic allowing individual transmitters to be deactivated. This allows RS-485 to implement linear bus topologies using only two wires. The equipment located along a set of RS-485 wires are interchangeably called nodes, stations or devices. The recommended arrangement of the wires is as a connected series of point-to-point (multidropped) nodes, i.e. a line or bus, not a star, ring, or multiply connected network. Star and ring topologies are not recommended because of signal reflections or excessively low or high termination impedance. If a star configuration is unavoidable, special RS-485 star/hub repeaters are available which bidirectionally listen for data on each span and then retransmit the data onto all other spans.
Ideally, the two ends of the cable will have a termination resistor connected across the two wires. Without termination resistors, reflections of fast driver edges can cause data corruption. Termination resistors also reduce electrical noise sensitivity due to the lower impedance. The value of each termination resistor should be equal to the cable characteristic impedance (typically, 120 ohms for twisted pairs). Somewhere along the set of wires, pull up or pull down resistors are established to fail-safe bias each data wire when the lines are not being driven by any device. This way, the lines will be biased to known voltages and nodes will not interpret the noise from undriven lines as actual data; without biasing resistors, the data lines float in such a way that electrical noise sensitivity is greatest when all device stations are silent or unpowered.
The EIA once labeled all its standards with the prefix "RS" (Recommended Standard), but the EIA-TIA officially replaced "RS" with "EIA/TIA" to help identify the origin of its standards. The EIA has officially disbanded and the standard is now maintained by the TIA as TIA-485, but engineers and applications guides continue to use the RS-485 designation.
RS-485 only specifies electrical characteristics of the generator and the receiver. It does not specify or recommend any communications protocol, only the physical layer. Other standards define the protocols for communication over an RS-485 link. The foreword to the standard recommends The Telecommunications Systems Bulletin TSB-89 which contains application guidelines, including data signaling rate vs. cable length, stub length, and configurations.
Section 4 defines the electrical characteristics of the generator (transmitter or driver), receiver, transceiver, and system. These characteristics include: definition of a unit load, voltage ranges, open circuit voltages, thresholds, and transient tolerance. It also defines three generator interface points (signal lines); "A", "B" and "C". The data is transmitted on "A" and "B". "C" is a ground reference. This section also defines the logic states 1 (off) and 0 (on), by the polarity between A and B terminals. If A is negative with respect to B, the state is binary 1. The reversed polarity (A +, B −) is binary 0. The standard does not assign any logic function to the two states.
Often in a master-slave arrangement when one device, the master, initiates all communication activity, the master device itself provides the bias and not the slave devices. In this configuration, the master device is typically centrally located along the set of RS-485 wires, with two slave devices located at the physical end of the wires providing termination. The master device itself could provide termination if it were located at a physical end of the wires, but that is generally regarded as a bad topology design as the master operates optimally when located at a halfway point between the slave devices, thereby maximizing signal strength and therefore line distance and speed. Applying the bias at multiple node locations could possibly cause a violation of the RS-485 specification and cause communications to malfunction.
Full duplex operation
RS-485, like RS-422, can be made full-duplex by using four wires. Since RS-485 is a multi-point specification, however, this is not necessary in many cases. RS-485 and RS-422 can interoperate with certain restrictions.
Converters between RS-485 and other formats are available to allow a personal computer to communicate with remote devices. By using "Repeaters" and "Multi-Repeaters" very large RS-485 networks can be formed. TSB-89A, The Application Guidelines for TIA/EIA-485-A has one diagram called "Star Configuration. Not recommended." Using an RS-485 "Multi-Repeater" can allow for "Star Configurations" with "Home Runs" (or multi-drop) connections similar to Ethernet Hub/Star implementations (with greater distances). Hub/Star systems (with "Multi-Repeaters") allow for very maintainable systems, without violating any of the RS-485 specifications. Repeaters can also be used to extend the distance or number of nodes on a network.
RS-485 signals are used in a wide range of computer and automation systems. In a computer system, SCSI-2 and SCSI-3 may use this specification to implement the physical layer for data transmission between a controller and a disk drive. RS-485 is used for low-speed data communications in commercial aircraft cabins' vehicle bus. It requires minimal wiring, and can share the wiring among several seats, reducing weight.
RS-485 is used as the physical layer underlying many standard and proprietary automation protocols used to implement Industrial Control Systems, including the most common versions of Modbus and Profibus. DH 485 is a proprietary communications protocol used by Allen-Bradley in their line of industrial control units. Utilizing a series of dedicated interface devices, it allows PCs and industrial controllers to communicate in a local area network utilizing a token passingmedium access control. These are used in programmable logic controllers and on factory floors. Since it is differential, it resists electromagnetic interference from motors and welding equipment.
In theatre and performance venues RS-485 networks are used to control lighting and other systems using the DMX512 protocol.
RS-485 is also used in building automation as the simple bus wiring and long cable length is ideal for joining remote devices. It may be used to control video surveillance systems or to interconnect security control panels and devices such as access control card readers.
It is also used in model railway: the layout is controlled by a command station using Digital Command Control (DCC). The external interface to the DCC command station is often RS-485 used by hand-held controllers or for controlling the layout in a network/PC environment. Connectors in this case are 8P8C / RJ45.
RS-485 is not a protocol; it's simply an electrical interface. Although many applications use RS-485 signal levels, the speed, format, and protocol of the data transmission is not specified by RS-485. Interoperability of even similar devices from different manufacturers is not assured by compliance with the signal levels alone.
The most common protocol in use is Asynchronous serial communication, but others are also in use e.g. Simple Sensor Interface protocol.
The RS-485 differential line consists of two pins:
- A aka non-inverting pin (but beware - see below)
- B aka inverting pin
An optional, third pin may be present (the TIA standard (ANSI/TIA/EIA-485-A, page 15, A.4.1) requires the presence of a common return path between all circuit grounds along the balanced line for proper operation) :
- SC aka G aka reference pin. (Discussed further below.)
The RS-485 standard states (paraphrased):
- For a MARK (logic 1), the driver's A terminal is negative relative to the B terminal.
- For a SPACE (logic 0), the driver's A terminal is positive relative to the B terminal.
The truth tables of most popular devices, starting with the venerable SN75176, show the output signals inverted. This has caused much confusion since, with most device manufacturers following the SN75176's lead.
These names are all in use on various equipment, but the actual standard released by EIA only uses the names A and B. The B line is positive (compared to A) when data is 1. However, due to the ambiguous standard (which refers to the A line as "non-inverting"), there is much confusion about which is which. The RS-485 signaling specification, confusingly, says that signal A is the non-inverting pin and signal B is the inverting pin. This is in accordance with the A/B naming used, incorrectly, by most differential transceiver manufacturers, including, among others:
- Texas Instruments, as seen in their application handbook on EIA-422/485 communications (A=non-inverting, B=inverting)
- Intersil, as seen in their data sheet for the ISL4489 transceiver
- Maxim, as seen in their data sheet for the MAX483 transceiver
- Linear Technology, as seen in their datasheet for the LTC2850, LTC2851, LTC2852
- Analog Devices, as seen in their datasheet for the ADM3483, ADM3485, ADM3488, ADM3490, ADM3491
- FTDI, as seen in their datasheet for the USB-RS485-WE-1800-BT
These manufacturers are all incorrect (but consistent), and their practice is in widespread use, so care must be taken when using A/B naming.
A common de-facto standard is the use of:
- TX+/RX+ or D+ as alternative for B (high for MARK i.e. idle)
- TX-/RX- or D- as alternative for A (low for MARK i.e. idle)
With Modbus, BACnet and Profibus, A/B labeling refers A as the negative green wire and B as the positive red wire, in the definition of the D-sub connector and M12 circular connector, as can be seen in Profibus guides. As long as standard excludes logic function of the generator or receiver, it would make sense A (green, negative) is higher than B (red, positive). However this contradicts the facts that an idle mark state is a logical oneand the termination polarization puts B at a higher voltage in Profibus guidelines. That so-called 'Pesky Polarity' problem  raised confusion which made authors think A is inverting within the TIA-485-A standard itself  and advise to swap what is A and B in drivers and line labeling as can be read in a section of an application bulletin: "Design Consideration #3: Sometimes Bus Node A Isn’t Really Bus Node A". It is now a common design decision to make this inversion which involves the following polarity chain: UART/MCU idle => TTL/CMOS = +5V => Line B voltage > Line A voltage, implying A, the green wire, is indeed connected to the driver inverting signal, as seen in a whitepaper.
RS-485 does not specify any connector or pinout. Circuits may be terminated on screw terminals, D-subminiature connectors, or other types of connectors.
The standard does not discuss cable shielding, but makes some recommendations on preferred methods of interconnecting the signal reference common and equipment case grounds.
In addition to the A and B connections, the EIA standard also specifies a third interconnection point called SC, which is the common signal reference ground. This connection may be used to limit the common-mode signal that can be impressed on the receiver inputs. This third signal is the reference potential used by the transceiver to measure the A and B voltages.
The allowable common-mode voltage is in the range -7V to +12V, i.e. +/-7V on top of the 0-5V signal range. Failure to stay within this range will result in, at best, signal corruption, and, at worst, device destruction. However care must also be taken that an SC connection, especially over long cable runs, does not result in an attempt to connect disparate grounds together - it is wise to add some current-limiting to the SC cable. Grounds between buildings may vary by a small voltage, but with a very low impedance and hence the possibility of catastrophic currents - enough to melt signal cables, PCB traces, and transceiver devices.
The diagram below shows potentials of the '+' and '−' pins of an RS-485 line during transmission of one byte (0xD3, least significant bit first) of data using an asynchronous start-stop method.
- ^Soltero, Manny; Zhang, Jing; Cockril, Chris; Zhang, Kevin; Kinnaird, Clark; Kugelstadt, Thomas (May 2010) . RS-422 and RS-485 Standards Overview and System Configurations, Application Report(pdf). Texas Instruments (Technical report). SLLA070D.
- ^Electronic Industries Association (1983). Electrical Characteristics of Generators and Receivers for Use in Balanced Multipoint Systems. EIA Standard RS-485. OCLC 10728525. [page needed]
- ^"DS3695,DS3695A,DS3695AT,DS3695T,DS96172, DS96174,DS96F172MQML,DS96F174MQML: Application Note 847 FAILSAFE Biasing of Differential Buses (Literature Number: SNLA031)"(PDF). Texas Instruments. 2011.
- ^"Trim-the-fat-off-RS-485-designs". EE Times. 2000.
- ^Thomas, George (March–April 2008). "Examining the BACnet MS/TP Physical Layer"(PDF). the Extension. Contemporary Control Systems, Inc. 9 (2).
- ^"DH-485 Industrial Local Area Network Overview". Rockwell Automation. Retrieved 10 September 2010.
- ^lenzusa.com, XpressNET FAQ, accessed July 26, 2015
- ^bidib.org, "BiDiBus, a Highspeed-Bus for model-railways", accessed July 26, 2015.
- ^"Polarity conventions"(PDF). Texas Instruments. 2003.
- ^"Data Sheet FN6074.3: ±15kV ESD Protected, 1/8 Unit Load, 5V, Low Power, High Speed and Slew Rate Limited, Full Duplex, RS-485/RS-422 Transceivers"(PDF). Intersil Corporation. 28 April 2006.
- ^"Data Sheet 19-0122 – MAX481/MAX483/MAX485/MAX487–MAX491/MAX1487: Low-Power, Slew-Rate-Limited RS-485/RS-422 Transceivers"(PDF). Maxim Integrated. September 2009.
- ^"LTC2850/LTC2851/LTC2852 3.3V 20Mbps RS485/RS422 Transceivers"(PDF). Linear Technology Corporation. 2007.
- ^"ADM3483/ADM3485/ADM3488/ADM3490/ADM3491 (Rev. E)"(PDF). Analog Devices, Inc. 22 November 2011.
- ^"USB to RS485 Serial Converter Cable Datasheet"(PDF). Future Technology Devices International Ltd. 27 May 2010.
- ^"Profibus Interconnection Guideline (PDF)". 1.4. P International. January 2007. p. 7. (Registration required (help)).
- ^"SIMATIC NET Profibus Network Manual (PDF)"(PDF). Siemens. April 2009. p. 157.
- ^"RS-485 Technical Manual, TIA-485 section". Wikibooks.
- ^"Profibus Interconnection Guideline (PDF)". 1.4. P International. January 2007. p. 8. (Registration required (help)).
- ^"RS-485 Technical Manual, That Pesky Polarity". Wikibooks.
- ^"RS485 Polarity Issues". Chipkins Automation Systems.
- ^"Application Bulletin AB-19, Profibus Compliance: A Hardware Design Guide"(PDF). NVE Corporation. 2010.
- ^"White paper: Polarities for Differential Pair Signals". Advantech B+B SmartWorx.
Understanding RS485 and RS422
Those familiar with RS232 will know that the standard defines how RS232 lines should be driven electrically: what they are called, what information they carry and even the connectors and pin numbers to use. RS422 and RS485, by contrast, define only the electrical characteristics of the driver.
Advantages of RS485 and RS422 | Differences between RS485 and RS422 | Wiring Arrangements | Preventing Voltage Reflection | Ideal RS485 Wiring | Line Pull Ups: Avoiding Serial Errors | Signal Names: Caution Required | Free RS485/RS422 Monitoring Software | Comments
Advantages of RS485 and RS422
RS485 and RS422 drive lines in a differential fashion: two wires are required for each signal. If you wish to transmit four signals then eight wires are needed. The figure below shows a single RS485 / RS422 signal being transmitted. To transmit a logic 1, line B is high and line A is low. To transmit a logic 0, line B is low and line A is high. The advantage of this arrangement is that signals can be transmitted faster and over greater distances than is possible with a single wire.
Diffences Between RS422 and RS485
In both RS422 and RS485, one driver can drive many receivers. In RS485 each driver can be switched off allowing multiple units to send data over a single pair of wires. This is not possible in RS422. This extra feature causes extra problems for RS485 units. Other differences are small so hereafter I will refer to units as RS485 but the remarks apply to RS422 also. Interface units often describe themselves as RS422/RS485 because a RS485 unit which is not using its extra capability is RS422 compatible.
RS485 Wiring Arrangements
When instruments are described as having an RS485 interface this tells you nothing for sure about the signals being transmitted. Usually though only the Transmit Data (TX) and Receive Data (RX) of a normal serial port are converted to RS485 or RS422. The other signals of the serial port are not used. Three arrangements are commonplace: Write only, 4-wire (full duplex) and 2-wire (half duplex).
Write Only System: Sending Data Only
In this arrangement the computer sends data out over a single RS485 pair of wires to many instruments. It never reads any data back. An example of this is the remote control of CCTV cameras. The operator can send out messages to move the camera. His feedback is the TV picture so no return data is needed. This requires only conversion of the RS232 TX signal to RS485.
Full Duplex System: Sending and Receiving Data over 4 Wires
Full Duplex means that data can pass simultaneously both to and from the instruments. This requires 4 wires - one pair to Transmit and one pair to Receive. The computer alone controls the TX transmit line. It sends out a message which includes an Address. The addressed instrument alone replies by driving the RX line.
This does mean that all the connected instruments must use the same software protocol - otherwise there will be confusion as to which instrument is being addressed. A simple conversion of RS232 to RS485 will suffice for this arrangement and no special demands are made on general purpose software such as ComDebug.
Half Duplex System: Sending and Receiving Data over 2 Wires
Half Duplex means that data can only pass in one direction at a time. In this arrangement both TX and RX signals share a single pair of wires. This can save in installation costs.
The computer drives the lines to send out its request message but must turn its driver off to allow the instrument to reply. This is the tricky bit. Many RS232-to-RS485 converters recruit the RTS line of the serial port to switch the RS485 driver On and Off. However Windows has never made more than a half hearted attempt to support such an arrangement.
The multi-tasking nature of Windows means that it is always difficult to make actions occur at exact times - in this case there can be a significant delay between the request being sent out and the driver being switched off. If the instrument starts its reply before the switch-off then the start of the reply will be missed. Instrument manufacturers are forced to find their own solutions to this problem. This may include special software, special hardware or both.
In recent years most Serial Ports have been implemented as USB-to-Serial arrangements. These units always include a microprocessor and this can perform the task of controlling the RS485 driver very well. If you need to implement a 2-wire RS485 system you should always obtain a USB-to-RS485 converter that advertises this special feature. An example type that we use is Moxa 1130. This unit automatically switches off the driver when there is no more data to send. Such a unit can work with general purpose software such as ComDebug or HyperTerminal. Be aware though that it may not work with the special software supplied by instrument manufacturers which may assume a particular RS232- to-RS485 converter and may produce errors when used with any other unit.
Preventing Voltage Reflection
When a signal is sent down a cable there is always a reflection voltage which returns up the cable. This reflection is bigger as signals' edges get faster and lines get longer. It can be minimised by terminating the ends of the line with the characteristic impedance of the system. This is 120 ohm for RS485.
Ideal RS485 Wiring
Ideally an RS485 system consists of a single linear cable (no branches) with 120 ohm resistors connected across the 2 wires at each end of the cable.
RS485 can handle speeds of over 10 Mbits per second and line lengths of over 1 km. If you are operating anywhere near these values you must arrange your wiring close to the ideal.
For many applications where baud rates are slow (say 9600 baud), and lines are only tens of meters long, this is not essential. The wiring requirements can then be relaxed to allow cables to run in star arrangement from the computer and the terminating resistors become optional.
Line Pull Ups: Avoiding Serial Errors
In many RS485 multidrop systems there are times when no unit is driving the RS485 lines. They can then go to any voltage and may produce serial errors. To avoid this it is often necessary to fit resistors which pull one line high and the other line low putting the line into the passive state. The RS485 converters usually include such resistors which can be connected if needed.
RS485 Signal Names: Caution Required
You will find that your RS485 signal names for a line pair are either A,B or +,-. In an ideal world you would simply connect A on the computer to A on the instrument. However these names are not consistently applied by manufacturers and you may need to connect A on the computer to B on the instrument.